Sydney Electrical & Data provides testing of emergency and exit lights to Australian Standard AS 2293.
AS/NZS 2293 requires emergency lights and exit lights to be tested every 6 months to ensure that they will function correctly in the case of an emergency.
It is essential that emergency lighting and exit lighting will operate from the internal battery for a minimum of 90 minutes in the case of power failure. This is to ensure the safe escape of people from buildings in case of an emergency such as a fire or earthquake.
As emergency lights and exit lights are operating on standby and chargng the battery 24/7, these are prone to failure after several years. That is why it is important that these fittings are discharge tested regularly.
We can also assist with the maintenance of your Stanilite Nexus emergency lighting system.
The most common brands of emergency and exit lights are:
- Stanilite (Thomas & Betts)
- Clipsal / Schneider
Sydney Electrical & Data conducts maintenance of emergency and exit lights including:
- Globe replacement
- Fluorescent tube replacement
- Battery Pack replacement
- Inverter / Contoller replacement
- Discharge Tests
- Compilation of emergency lighting test logs